Dimension (Length x Width x Depth): 180 x 100 x D43cm
Bath Option Available:
The size of this Phoenix Rectangularo 7 Rectangular Bath are:
ELECTRICAL CONNECTION - THIS SHOULD BE CARRIED OUT BY A QUALIFIED ELECTRICIAN
Supply requirements - 240v, 13amp, live, neutral, earth. Wiring must comply with all regulations for electrical wiring as published by the institute of Electrical Engineers. The supply must be via an earth leakage circuit breaker/residual current device (ELCB, RCD, RCCB) rated at 20amp minimum with a 30milliamp trip current. The supply should be installed on a switched fused spur which, together with the RCD, should be fitted outside the room where the bath is installed.
If an Inline Heater is fitted the electrical rating is 1.5 KW Each individual pump/blower or optional extra (light & Inline heater) all have a separate electrical cable to supply the power.
Make sure that all cables are connected via an IP55 rated junction box.
There is no need to remove either the motor terminal block cover, the timer control box cover (if fitted), or the electronic control box cover (if fitted). Doing so without authorisation from Phoenix Whirlpools Ltd will invalidate the warranty.
The supply should be checked to ensure earthing is in existence and is satisfactory.
The above are general guidelines for Phoenix Whirlpool baths and the full installation instructions should be followed.